The expansion joint technology of ventilation pipeline is a non excavation local collar repair method. The main materials used in this technology are annular rubber water stop sealing belt and stainless ventilation pipe expansion joint. Rubber ring double expansion ring is installed at the pipe interface or local damaged part. After the ventilation pipe expansion joint is in place, it is fixed with 2-3 ventilation pipe expansion joints to achieve water stop. The expansion joint of the ventilation pipeline has fast construction speed, good quality stability, and can withstand interface dislocation. The anti internal pressure effect of the water stop collar is better than that of the external pressure, but it has an impact on the water flow pattern and the cross-section. In the non excavation of the drainage pipeline, it is usually used in combination with the drilling grouting method. The expansion joint of the ventilation pipe is mainly used for water leakage at the interface of the large-diameter pipe (the pipe diameter is not less than 800mm). The general process is as follows: according to the inner diameter of the pipe, first customize the stainless steel strip and rubber strip in the factory, and then enter the pipe for installation. First fix the rubber strip manually, and then press the expansion joint of the ventilation pipe with the sealing rubber ring through the pipe, so as to complete the local anti-seepage of the pipe. If necessary, grouting can be carried out for the leakage of the pipe.
Expansion joint of ventilation duct
1. It is determined that it is necessary to install the expansion joint of the ventilation pipe. The expansion joint of the ventilation pipe shall be placed in the inspection shaft at the upstream and downstream of the pipe section to ensure that the water supply in the pipe section to be temporarily cut off;
2. Clean the pipeline;
3. Since the pipe diameter is DN800, the staff directly enter the pipeline to determine the position;
4. Prepare the materials of the expansion joint of the ventilation pipe. First, put the annular rubber lining on the pipe surface, and then close the expansion joint of the ventilation pipe to the annular rubber to fix it on the pipe surface. After the process is completed, confirm that all the water leakage points are sealed;
5. TV endoscope inspection (or manual photo taking) to determine whether the pipe section has been recorded;
6. Pavement recovery;
Expansion joint of ventilation duct
7. Sort out the completion data and put it on record.
Requirements for use of expansion joints of ventilation pipes:
(1) When designing the expansion joint of the ventilation pipe, the pipe diameter of the original pipe shall be determined first to ensure the correction relationship between the outer diameter of the expansion joint of the ventilation pipe and the inner diameter of the pipe.
(2) When the local lining method of ventilation pipe expansion joint is adopted for construction, the design and fabrication width of ventilation pipe expansion joint shall meet the length of the pipe section.
(3) The expansion joint of the ventilation pipe is used together with the old pipe to form a composite pipe. The design wall thickness of the inner liner pipe meets the leakage pressure requirements of the old pipe to damage the groundwater.
The above is the detailed introduction of Jinan ventilation duct. I hope it will help you. If you have any questions, please contact us. We will provide you with services with a professional attitude http://www.rps-infinia.com